90.92 Standard to be revised Apr 28, 2020
CEN/TC 269 Shell and water-tube boilers
27.060.30 Boilers and heat exchangers
This European Standard applies to shell boilers with volumes in excess of 2 litres for the generation of steam and/or hot water at a maximum allowable pressure greater than 0,5 bar and with a temperature in excess of
The purpose of this European Standard is to ensure that the hazards associated with the operation of shell boilers are reduced to a minimum and that adequate protection is provided to contain the hazards that still prevail when the shell boiler is put into service. This protection will be achieved by the proper application of the design, manufacturing, testing and inspection methods and techniques incorporated in the various parts of this European Standard. Where appropriate, adequate warning of residual hazards and the potential for misuse are given in the training and operating instructions and local to the equipment concerned (see EN 12953-7 and EN 12953-8).
It is the manufacturer's responsibility, in addition to complying with the requirements of this standard, to take into consideration special measures which could be necessary in order to achieve by manufacturing the required level of safety in accordance with the EU Directive 97/23/EC (PED).
NOTE 1 Further requirements relating to operating instructions in prEN 12953-13 and to hazard analysis in
CEN/TS 764-6 should be taken into consideration.
This European Standard specifies requirements for both directly fired and electrically heated boilers including Low Pressure Boilers (LPB, see 3.6) as well as for heat recovery boilers with a gas-side pressure not exceeding 0,5 bar of cylindrical design, constructed from carbon or carbon manganese steels by fusion welding and a design pressure not exceeding 40 bar. The boilers covered by this European Standard are intended for land use for providing steam or hot water (typical examples are shown in Figures 1 to 6).
For Low Pressure Boilers (LPB) less stringent requirements concerning design and calculation are acceptable. Details are defined in the respective clauses.
NOTE 2 For boilers operating at a pressure on the gas-side greater than 0,5 bar the rules of this standard equally apply. However, it is generally considered that additional design analysis, inspection and testing may be necessary.
Where a particular boiler is a combination of shell and water-tube design then the water-tube standard series EN 12952 is used in addition to this European Standard. One such example of this combination is shown in Figure 3.
This European Standard applies to the generator, from the feed-water or water inlet connection to the steam or water outlet connection and to all other connections, including the valves and steam and water fittings. If welded ends are used, the requirements specified herein begin or end at the weld where flanges, if used, would have been fitted.
This European standard does not apply to the following types of boilers and equipments:
a) water-tube boilers;
b) non stationary boilers, e.g. locomotive boilers;
c) thermal oil boilers;
d) boilers where the main pressure housing is made of cast material.
e) pumps, gaskets, etc.
f) brickwork setting and insulation, etc.
NOTE Stainless steel boilers are covered by EN 14222.
Legislation related to this standard
Directive 2014/68/EU of the European Parliament and of the Council of 15 May 2014 on the harmonisation of the laws of the Member States relating to the making available on the market of pressure equipmentHarmonized/Supporting
90.92 Standard to be revised
Apr 28, 2020