60.60 Standard published Oct 16, 2019
CEN/TC 107 Prefabricated district heating and district cooling pipe system
23.040.07 Pipelines and its parts for district heat
This document specifies requirements and test methods for fittings of factory made thermally insulated bonded twin pipe assemblies for hot water networks in accordance with EN 13941 1, comprising two steel service fittings and/or valves, polyurethane foam thermal insulation and one casing of polyethylene.
The pipe assembly can also include the following additional elements: measuring wires, spacers and diffusion barriers.
This document covers the following assemblies:
- fittings: bends, T-pieces and reducers;
- valve construction.
This document applies to fitting and valve assemblies with a minimum design pressure of 1,6 MPa (overpressure).
60.60 Standard published
Oct 16, 2019