This part of EN 14511 specifies minimum requirements which ensure that air conditioners, heat pumps and liquid chilling packages with electrical driven compressor, are fit for the use designated by the manufacturer when used for space heating and/or cooling.
This European Standard applies to factory-made units that can be ducted.
This standard applies to factory-made liquid chilling packages with integral condensers or for use with remote condensers.
This standard applies to factory-made units of either fixed capacity or variable capacity by any means.
Packaged units, single split and multisplit systems are covered by this standard, except water cooled multisplit systems.
In the case of units consisting of several parts, the standard applies only to those designed and supplied as a complete package, except for liquid chilling packages with remote condenser.
This standard is primarily intended for water and brine chilling packages but can be used for cooling any other liquid subject to agreement.
This standard applies to air-to-air air conditioners which evaporate the condensate on the condenser side.
The units having their condenser cooled by air and by the evaporation of external additional water are not covered by this standard.
This standard does not apply to units using transcritical cycles, e.g. with CO2 as refrigerant.
Installations used for heating and/or cooling of industrial processes are not within the scope of this standard.
NOTE Part load testing of units is dealt with in CEN/TS 14825.
Directives related to this standards.
Commission Directive 2002/31/EC - Implementation of Coucil Directive 92/75/EEC with regard to energy labelling of household air-conditioners
Indication by labelling and standard product information of the consumption of energy and other resources by household appliances